Bio particle control (Bacteria, mold , Fungi)
Safe & Secure
Dustkiller®-Bio o is a dust and bio-particle controller used as a primary or supplementary device in any room where dust control and bio-particle control is required. These devices may be used in Operation Theatres, Intensive Care Units, Patient Care rooms, Recovery rooms and similar areas. Standard sterilization and disinfection procedures such as fumigation, germicidal UV sterilization, wipe-down, etc are used in all or some of the above areas to control dust as well as bio-particles. Once these procedures are over, the room starts deteriorating over time. By installing and running Dustkiller®-Bio units in these areas (the number of units will be based on the criticality of dust and bio-particle control in the room), we can maintain good control of pollutants in the room over time as long as the Dustkiller®-Bio units are in operation. The units can be left running continuously for excellent control results .
How it Works
(Electrical power should be disconnected ) Regular maintenance of the Dustkiller®-Bio units should be carried out by trained personnel . The electrostatic filter modules are to be washed periodically using pressurized water at around 110bar near an Effluent Treatment Plant . The UV lamps and sensors are to be wiped with a dry , clean lint-free cloth . The pre and post filter media is not washable but is to be replaced periodically . AC mains power ON ,UV lamps fault as well as machine fault indicators(9) are provided along with an LCD display(optional) which indicates the particle count in the room for PM2.5 and PM10 particles (approximate running average value) . Castor wheels(10) are provided for portability.
|Technical Specifications for Dustkiller®-Bio Model DKB500DP
|Model : DKB500DP
|Air flow capacity
|500 Cu mtrs per hour(CMH)
|230Volts + /- 10% , 50Hz
|50watts - power pack for electrostatics & control electronics 140watts – suction fan
|Filtration method and filter type
|Pre filter : MS frame with reticulated foam impregnated with silver (Ag)and titanium dioxide(TiO2) nano particles. TiO2 nano particles activated by UV light .Not to be washed. Replace periodically.
|Post filter : MS frame with reticulated foam impregnated with silver (Ag)and titanium dioxide(TiO2) nano particles. TiO2 nano particles activated by UV light. Not to be washed. Replace periodically.
|Filter Modules: 2nos electrostatic modules ( Al , SS, ceramic). Many times washable and re-usable.
|Better than 95% for atmospheric dust and bio particles
|Germicidal , 15 watts each (4 nos)
|3 nos grill sections at the sides and front towards lower part of the enclosure
|Clean Air outlet / Noise level dB
|Grill section at the top of the enclosure facing front/62dB
|UV lamp fail indicator , PM2.5 & PM10 particle count LCD (with acceptable/not acceptable) display(optional)
|440 x 410 x 1150 (including wheels)